Our Photoluminescent Glow in the dark Signs can be installed as stand alone emergency evacuation signage, or they can compliment existing Exit signage. All of our Photoluminescent Exit Signs are also suitable for floor proximity installations without requiring any additional electrical wiring.
There are clear advantages to our products.
NightBright USA photoluminescent ETL listed to standard UL 924 Exit signs are more stable, physically robust and have a better chemical makeup as compared to aluminate or aluminosilicate phosphorescent crystal signs. Our product’s glow in the dark photoluminescence outperforms comparable phosphors products in terms of durability, afterglow brightness and afterglow duration. NightBright USA guarantees the photoluminescent properties of our aluminum Exit signs and other aluminum products for up to 30 years when installed indoors. Our proprietary printing method produces a more dynamic luminescence value, and an overall higher quality exit and evacuation sign. NightBright USA uses a sturdy 100% recyclable eco friendly aluminum substrate which resists ultra high temperatures, and allows for the sign to maintain its glow during a fire. Plus our products qualify for three LEED credit criteria.
PHOTOLUMINESCENT EXIT SIGNS (MODELS ULG-050, ULB-050 AND ULR-050)
Installation, Maintenance and Operating Instructions
Caution: Sign Requires external illumination
“SAVE THESE INSTRUCTIONS FOR FIRE SAFETY INSPECTION”
At the face of all our exit signs there must exist at least a 54 lux (5 foot-candle) source of illumination. This source must be reliable and remain active at the location where the sign is installed at all times that the building is occupied. Movement sensor and/or timers are not allowed for purpose of illumination.
Signs are to be fixed onto walls, doors or ceiling by means of tamper proof screws. When using tamper proof screws it may be also appropriate to use in addition an adhesive such as Liquid Nails.
If the sign is supplied with frames for ceiling or wall installation, the frames are to be installed prior to placing the sign in the slot supplied and then fixed by means of set screws provided.
Chevrons indicating direction of exit are supplied with the sign. The sign has guides for installation of such chevrons; follow the dots printed making sure that the chevrons are mounted straight. To install chevrons please remove the top protection on the adhesive and place in the proper place as indicated by dots.
Since signs are photoluminescent, once they have been charged with a light source, they will automatically glow when lights go out.
These instructions are for indoor installations.
Clean as needed with water damped cloth, neither chemicals nor solvent are to be used.
Maintenance should assure that lighting is in accordance with above instructions making sure that nothing obstructs the adequate lighting condition required.
IF THERE MAY BE ANY DOUBT WHATSOEVER PLEASE CONTACT OUR HEAD OFFICES AT 888-987-2336 OR EMAIL US AT firstname.lastname@example.org
4711 Hwy 36 S. Suite 44, Rosenberg, TX 77471 USA
Phone: 713-596-8085 Website: http://nightbrightusa.com
Photoluminescent Sign Products and OSHA ANSI Signs
All of our products are Code Compliant with the latest versions of:
| IBC 2012 | IFC | ICC | NFPA 2012 | OSHA | M.E.A. |
| STD. UL 924 | STD UL 1994 | ASTM | ISO |