Our Photoluminescent Path Markers can be installed as stand alone evacuation Path Markers, or they can compliment existing Evacuation Systems. All of our Photoluminescent Path Markers require no additional electrical wiring.
Click below to see our other
Photoluminescent Product Lines
Fire Emergency Signs
Fire Extinguisher Signs
Stair ID & Evacuation Maps
There are clear advantages to our products.
NightBright USA signs are more stable, physically robust and have a better chemical makeup as compared to aluminate or aluminosilicate phosphorescent crystal signs. Our product’s photoluminescence outperforms comparable phosphors products in terms of durability, afterglow brightness and afterglow duration. NightBright USA guarantees the photoluminescent properties of our aluminum products for up to 30 years when installed indoors. Our proprietary printing method produces a more dynamic luminescence value, and an overall higher quality sign. NightBright USA uses a sturdy 100% recyclable eco friendly aluminum substrate which resists ultra high temperatures, and allows for the sign to maintain its glow during a fire. Plus our products qualify for three LEED credit criteria.
PHOTOLUMINESCENT EXIT SIGNS (MODELS ULG-050, ULB-050 AND ULR-050)
Installation, Maintenance and Operating Instructions
Caution: Sign Requires external illumination
“SAVE THESE INSTRUCTIONS FOR FIRE SAFETY INSPECTION”
At the face of all our exit signs there must exist at least 54 lux (5 foot-candle) source of illumination. This source must be reliable and remain active at all times that the building WHERE THE SIGN IS INSTALLED IS OCCUPIED. Movement sensor and/or timers are not allowed for purpose of illumination.
Signs are to be fixed onto walls, doors or ceiling by means of tamper proof screws. When using tamper proof screws it may be also appropriate to use in addition an adhesive such as Liquid Nails.
If the sign is supplied with frames for ceiling or wall installation, the frames are to be installed prior to placing the sign in the slot supplied and the fixed by means of set screws provided.
Chevrons indicating direction of exit are supplied with the sign. The sign has guides for installation of such chevrons; follow the dots printed making sure that the chevrons are mounted straight. To install chevrons please remove the top protection on the adhesive and place in the proper place as indicated by dots.
Since signs are photoluminescent, once they have been charged with a light of source, they will automatically glow when lights go out.
These instructions are for indoor installations.
Clean as needed with water damped cloth, neither chemicals nor solvent are to be used.
Maintenance should assure that lighting is in accordance with above instructions making sure that nothing obstructs the adequate lighting condition required.
IF THERE MAY BE ANY DOUBT WHATSOEVER PLEASE CONTACT OUR HEAD OFFICES AT 888-987-2336 OR EMAIL US AT firstname.lastname@example.orgNightBright USA
4711 Highway 36 S. Suite 44 Rosenberg, TX 77471 US
Phone: 713-596-8085 Website: http://nightbrightusa.com
UL 924 Photoluminescent Exit Signs
Photoluminescent Tapes and Path Markers